Stop fried electronics - Page 2
This ground connection is crucial for proper operation, providing a shunt path for excess energy as well as a ground reference at the same potential as the host. In most cases, this means the ground connection should be made from the surge suppressor directly to the chassis of the host device. The impedance of the ground connection is critical. The voltage presented to the data port is equal to the clamping voltage of the surge suppression device plus the voltage drop in the suppressor's ground path to the node being protected. Any voltage drop in the ground connection will effectively increase the clamping voltage seen at the data port. Transient currents can be very large, with magnitudes measured in thousands of amps. At these current levels, the DC voltage drop (I X R) can be very large.
For example, 6 feet of 18AWG wire has approximately .039 Ω resistance. Although this initially appears to be a good ground connection, calculating I X R with a 3000 amp transient yields a voltage of 117 volts across the ground wire – enough to destroy any data port. To make matters worse, at the frequencies illustrated in Figures 1-3, the inductance of the ground wire causes an additional voltage drop that can be much higher than the I X R voltage drop. To minimize this voltage drop the ground connection should be made with heavy gauge wire and kept as short as possible. If the cable must be longer than one meter, braided cable intended for grounding purposes must be used.
Selecting a Surge Suppression Device
Two basic types of surge suppression products are available as illustrated in Figure 4. In either case, the system designer should consider the clamping voltage of the unit as well as its physical attributes, such as connector type and method of making the grounding connection.
Single Stage Devices
The most common device uses a single TVS or MOV for each protected line. This type of unit is usually small and inexpensive. If a proper ground connection is made, they should offer protection against most transients. A disadvantage of this device is that if a large transient damages one or more of the components there often is no indication that the unit has failed, leaving the node unprotected against future transients.
Three Stage Devices
More advanced units use three components on each protected line to handle much larger surge currents and to provide internal self protection, reducing the risk of undetected failures. The first stage is a gas discharge tube; this stage can shunt very large currents, but is slow reacting and requires a relatively large voltage before conduction begins. The second stage is series impedance; this stage limits the current flowing into the final stage of the circuit. Finally, a TVS device clamps at a voltage acceptable for the data port and maintains the clamp until the gas discharge tube begins conduction.
Protecting a system against transients with surge suppression requires attention to the selection as well as the installation of the suppression device. Any surge suppressor can be rendered ineffective if proper grounding techniques are not carefully followed. Confronting these issues early in the system design can reduce potentially time and money consuming problems before they occur.
About the Author
Mike Fahrion, director of product management at B&B Electronics is an expert in data communications with 20 years of design and application experience. He oversees development of the company’s rugged M2M connectivity solutions for wireless and wired networks based on serial, Ethernet, wireless and USB communication technology. Fahrion has particular experience in reliable connectivity solutions for devices deployed at the “edge” of networks in remote, harsh or uncontrolled environments. He is a speaker and widely published author. He holds a BSEE from Iowa State University.